AC, Furnace, & Plumbing Repair in O’Fallon, MO
O’Fallon Residents Feel Right at Home with Budget
Seeing a polar bear walk through a park or backyard in O’Fallon could reasonably be called a rare sighting.
A frequent sighting, on the other hand, is a truck from Budget Heating, Air Conditioning & Plumbing parked in someone’s driveway or in front of their home. That’s because we’re in your town virtually every day, bringing our unique home comfort skills and experience to bear for increased comfort, convenience, and safety.
In addition to our full slate of services, we also provide:
- Guaranteed upfront price for all service and repair work
- We’re committed, as individuals and a company, to your complete satisfaction
- All employees are background checked and drug screened
- All repair work – parts and labor included – is warrantied for 1 year.
*This warranty does not apply to Home Warranty repair work.
for O'Fallon, MO
Our Reviews by City
Marshall - O'Fallon, MO
Replaced my water heater under home warranty.. service from budget was professional.. installers were friendly and acknowledgable of work needed. They did a good job and kept the area clean when install was completed. My only disappointment was the extra out of pocket cost to me due to st Charles county requirements. $800.00 was not expected. Being a senior, this amount was hard to budget into house operatons since the home warranty was to take care of this issue.. No discount was offered by Budget heating and cooling. Overall..good service despite the out of pocket expenses.
Denise - O'Fallon, MO
Beau was courteous, knowledgeable and professional. He explained what was wrong and how it would be repaired.
Harold - O'Fallon, MO
Would recommend this serviceman to family and friends.
Amanda - O'Fallon, MO
Helped me understand everything by explaining what needs to be done.
service tech was nice and explained it was not covered under warranty
Jason - O'Fallon, MO
Home warranty was not covered even though I told them what was the issue. Tech that came out can not be blamed. He was nice and courteous. Issue is with what is covered with home warranty
Generald - O'Fallon, MO
The tech was very knowledgeable of our system. He gave us good advise as well. Very friendly and our air is back up an running.
Sellers - O'Fallon, MO
Great Service in a timely manner.
K - O'Fallon, MO
The Budget Technician made sure to make us aware of his arrival time and gave us updates throughout the repair process. He arrived at the expected time and was courteous. The water heater was repaired successfully in a timely manner
Dolly - O'Fallon, MO
He was great
Speedy, Great Service
Michelle - O'Fallon, MO
The guy was very friendly and was sure to explain and show me the issue. Fixed it in no time!
Troyer - O'Fallon, MO
Ashley was great - professional and efficient!
Joe - O'Fallon, MO
Brackman - O'Fallon, MO
Johnny - O'Fallon, MO
Can't be more satisfied with the quality of work that Mike did!
Outstanding Service. Very good price!
Stroot - O'Fallon, MO
Greg provided us with a very thorough summary of options available to us. And we felt it was a very reasonable price for a new furnace and air conditioner. We were very pleased with his professionalism.
Jeff was Great!
Andrew - O'Fallon, MO
Great service. Greg explained everything fully before performanlng Maintence. Thanks for getting our cold on!!!!
Moriarty - O'Fallon, MO
Shannon - O'Fallon, MO
My tech was so thoughtful and informed. Thank you!
Professional and great service
Marjore - O'Fallon, MO
Great service very pleased
Highfill - O'Fallon, MO
Friendly and helpful
Tara - O'Fallon, MO
Good, efficient and polite service.
Cthelma - O'Fallon, MO
repairman very curteous did a great job explaining cleaned up after himself my husband very impressed with him my husband told me to be sure to give him all 5 stars which is what I did if I could give a higher rating I would do so
Shipley - O'Fallon, MO
Greg very good
Ana - O'Fallon, MO
Ross was very good!Great service
Guerrero - O'Fallon, MO
Greg was very professional. Thanks
HVAC technician, heating, furnace repair. O'fallon, MO. Cleaned furnace out. Pulled and cleaned all burners. Found one burner was bent out.Was able to repair. Cleaned flame sensing rod. Checked all safetys. Test fired system all kicked in. System is heating.
Plumber, plumbing, water heater replacement. Water heater installation.
HVAC technician, heating, Furnace repair. Carrier. Found draft inducer motor bad.
HVAC technician, cooling, air conditioner repair. O'Fallon, MO. Found filter dirty pulled it. Blower good. Drain good. Gave call for cool. Fan motor locked up. Replaced 1/4hp 1075rpm motor. Test fired all kicked in. Pressure 74 and 243. System cooling.
Plumber, plumbing, faucet replacement, faucet installation. Kitchen Faucet Replacement: Basic. Upon arrival the customer stated that their kitchen faucet wasn’t working properly. Upon inspection I found that the faucet on both sides were clogged and had poor water flow. Since the faucet was a no name brand, I couldn’t replace the cartridges due to the no name brand. Did tried to use the delta style of faucet cartridge, but leaked. Decided to put a new faucet in. Replaced faucet, checked for leaks and proper operation. OK Bathroom Faucet Replacement: Bathroom Basic Another issue was in the upstairs hallway bathroom faucet. The handles were broken due to the cartridges were very hard to turn. Since this was a no name brand faucet, decided to replace it with a new one. Installed new faucet, checked for leaks and proper. OK
HVAC technician, cooling, air conditioner repair. O'Fallon, MO. Change filter. Lower good. Drain only 1/2” only. Gave call for cool. All kicked in. Pressure 45 and 187. Added 2 pounds r-22 with stop leak. Pressure is now 73 and 234. System cooling.
Plumber, plumbing, water heater replacement. Water heater installation.
HVAC technician, heating, furnace maintenance, O'Fallon, MO. Did clean and check. Cleaned all burners and cleaned flame sensing rod. Hot surface is good. All safety’s are good. Flue is not good. Rusted threw. Highly recommend getting replaced. 5” flue 200.00 to repipe. Gave call for heat. All kicked in. Flue needs to be replaced bc it could be a health hazard. Water heater pipe is not up to code. To much pitch for flue. Also flue is touching gas line. Expansion tank is not 14” away from cold line.
HVAC technician, heating, furnace repair. O'Fallon, Mo. Cleaned furnace. Filter needs to be switched. Pulled burners cleaned with wire brush. Check heat exchanger out with camera. Cleaned flame sensing rod. Checked all safety’s. Noticed swivel t 5” is starting to rust threw. Everything is safe to use and recommend. Replacing flue. System is heating.
HVAC technician, cooling, air conditioner repair, capacitor replacement, O'fallon, MO. Found cap was old. Replaced with new 55/5. Test fired and all came on. Humidifier pad was upside down. Fixed that issue as well. Showed customer how to install correctly. System pressure 78 and 255. System cooling.
HVAC technician, cooling, Air conditioner repair. BDP company. Repair wires on contactor for compressor
HVAC technician, cooling, air conditioner repair. O'fallon, MO. Pies is coming from drain line hose. Makes a gurgling noise. Negative pressure no trap in drain. Could repipe to 3/4” pvc for 200.00. Showed customer easy fix to salve issue. By putting a trap in the vinyl tubing. Explain how to fix. Pressure on ac unit is 74 and 223. System cooling.House temp 75
HVAC technician, heating, furnace repair. O'fallon, MO. Found plate on furnace is cracked. Blower wheel is also bad. Furnace needs to be replaced. A-coil pan is rusted threw and coil on slap is falling apart When ever the ac is running water is running directly down into the heat exchanger. Need to replace a-coil and furnace Ac out side runs off r-22. Gave customer quotes of upgrading system. If goes just with home warranty willing to do recommend replacing ac unit for 1600.00. Standard guardian system 5 ton.
Plumber,plumbing, pipe repair, Water line repair.
HVAC technician, cooling, air conditioner repair. O'Fallon, MO. Found cond fan motor locked up. Replaced with 1/3 hp. 1075rpm and 7.5 cap. Test fired all kicked in. Pressure 74 and 231. System cooling
O'Fallon, MO. 2nd floor system. Found blower good. Drain good. Filter pulled. Gave call for cool. Fan motor locked up. Replaced with 1/4 1075 rpm motor 7.5 cap. Test fired all kicked in. Pressure 72 and 215. System cooling. 8’ in air.
HVAC technician, cooling, air conditioner repair. O'fallon, MO. System 2 pounds low on charge. 410a ref. Pressure now 124 and 243. System is cooling
HVAC technician, cooling, air conditioner repair. O'fallon, MO. Found blower good. Drain good. Recommend 3/4” pvc . Filter good. Gave call for cool. All kicked in. Pressure 58 and 198. Added 2 pounds 410a with stop leak. Pressure now 118 and 243. System is cooling
HVAC technician, cooling, air conditioner repair. O'fallon, MO. Found blower good. Drain good. Recommend 3/4” pvc 150.00 to fix. Filter good. Gave call for cool. System had 24v but not 240v passing. Contactor bad. Replaced with double pole. Test fired all kicked in. Pressure 71 and 206. System cooling
HVAC technician, cooling, air conditioner repair. O'fallon, MO. Found pressure low on charge. 40 and 163. Added 3 pounds r-22 with stop leak. Pressure now 69.7 and 206. System is cooling.
Plumber, plumbing, Drain pipe repair.
Plumber, plumbing, Drain pipe repair.
HVAC technician, air conditioenr repair. O'fallon, MO. Found blower good. Filter good. Drain good. Gave call for cool. Cap old. Replaced 55/7.5. Test fired all kicked in. Pressure 77 and 253. System cooling.
HVAC technician, cooling, air conditioner repair. O'fallon, MO. Found filter dirty pulled it. Blower good. Drain good. Gave call for cool. Cap was old. Replaced with 45/5. Test fired all kicked in. Pressure 76 and 255. System cooling.
HVAC technician, cooling, Air conditioner repair. Trane. Replaced TXV in system.
Furnace Maintenance, Repair, and Installation Services O’Fallon, MO
When the heat goes, typically so does your patience. Especially if you’re having trouble finding a qualified HVAC repair person to assist you.
At Budget, we take care of heating problems large and small to help minimize any lack of comfort and frustration you might be feeling.
Of equal if not greater value, however, is our heating system preventative maintenance service. It’s designed to prevent problems, or spot and take care of small problems before they get any worse. Annual maintenance also leads to:
- Longer system lifespan
- Consistent temperatures from room to room
- Lower heating utility costs
- Added safety
If you heating system is on the way out, or already there, Budget can custom design and install the ideal heating system for your home, family, and budget. Plus, we provide free in-home consultations and proposals.
A/C System Maintenance, Repair, and Installation Services O’Fallon, MO
We offer the timely and professional services you need to keep you and your family comfortable, all cooling season long:
- Annual preventative maintenance
- High quality repairs
- New Air Conditioner Installation
- Whole-house humidifiers
- And more
What’s not to love about that? We can also help keep your system in top working order once you join ourHVAC Savings Club. As part of your low annual membership fee, you’re entitled to annual preventative maintenance…even better, we call you to schedule service so you don’t have to worry about it slipping your mind.
Plumbing Service, Repair, and Installation Services O’Fallon, MO
For greater convenience, you also can count on Budget for all your home plumbing needs. That means one less number to call, and one company you can depend on for heating, cooling, and plumbing alike.
Our many plumbing services include the following:
Recent federal regulations have changed the way we’ll all buy water heaters from now on, and we’re here to explain all of your options. We can also ensure you receive an annual whole-house plumbing inspection, plus a 15% savings on plumbing repairs, once you join our Budget Savings Club. Member customers love all the benefits it provides, and we’re confident you will, too.
For plumbing, heating, cooling, and related services that you can depend on, along with the people who provide them, contact Budget today.